Xpert Services for Transformers
What is Partial Discharge (PD) and what are the different types of Partial Discharges in power cables?
About ROC and Least Squares Fit
ROC (Rate of Change) is a measurement of gas generation rate; the rate at which gas-in-oil (ppm) levels change over a specific period of time. At minimum, the last three days of ppm measurements are used to make this calculation. ROC is calculated by fitting a minimum number of ppm measurements to a straight line using a standard least squares fit method. The slope of the calculated straight line is reported as the ROC, in ppm/day.
The calculated ROC can be used to generate a caution or alarm event for each gas and the total dissolved combustible gas (TDCG). TDCG is defined as: H2 + CH4 + C2H6 + C2H4 + C2H2 + CO. Along with ROC a “goodness of fit” indicator is calculated, which represents the scatter associated with the data points relative to their resulting least squares fit line.
Download the Whitepaper Below